INTERNATIONAL. STANDARD. IEC. Second edition. Telecontrol equipment and systems œ. Part Telecontrol protocols. IEC TASE.2 compliance and verification. Prove the quality and interoperability of your TASE.2 systems. Contact us: Elena Henriquez. Head of Section. Our IEC (TASE.2/ICCP) Source Code Library provides a quick and cost effective way to implement a Client, Server, or Bi-Directional TASE.2/ICCP.
|Country:||Central African Republic|
|Published (Last):||3 March 2013|
|PDF File Size:||11.55 Mb|
|ePub File Size:||15.98 Mb|
|Price:||Free* [*Free Regsitration Required]|
A typical national power grid ief a hierarchy of control centres to manage the generation, transmission, and distribution of power throughout the grid:. Prior to the development of electronics and telecommunications networks all co-ordination between control centres was carried out by telephone. However, the development of SCADA supervisory control and data acquisition systems allowed remote control and monitoring of electrical plant from centralised control centres.
Initially individual SCADA manufacturers developed their own proprietary “closed” protocols for communicating from a control centre to electrical equipment in the field. However, none of these communication protocols were suited to the requirements of communicating between control centres.
To meet these special requirements for communication and co-ordination between control centres the IEC developed the IEC set of standards. IEC part 6 is one of the IEC set of standards which define systems used for telecontrol supervisory control and data acquisition in electrical engineering and power system automation applications.
ICCP is also an international standard: Inter-utility real time data exchange has become critical to the operation of interconnected systems in most parts of the world.
For 608870-6, the development of electricity markets has seen the management of electricity networks by a functional hierarchy that is split across boundaries of commercial entities. At the top level there is typically a system operator with coordination responsibilities for dispatch and overall system security.
Below this are regional transmission companies that tie together distribution companies and generating companies. In continental power systems there is now considerable interconnection across international borders. 68070-6 allows the exchange of real time and historical power system information including status and control data, measured values, scheduling data, energy accounting data and operator uec.
Historically there has been reliance on custom or proprietary links and protocols to exchange real time data between systems. ICCP began as an effort to develop an international standard for real-time data exchange within the electric power utility industry. A working group was formed in to iex a protocol standard, develop a prototype to test the specification, submit the specification to the IEC for standardisation and carry out interoperability testing between developing vendors.
The initial driver was to meet European Common Market requirements in The official designation of the first protocol was TASE.
In the US, ICCP networks are widely used to tie together groups of utility companies, typically a regional system operator with transmission utilities, distribution utilities and generators.
Regional operators may also be connected together to co-ordinate import and export of power between regions across major inter-ties. The objects that are used to convey the data are defined in various parts of IEC 60870–6 Data transfers result from a request from a control centre client to another control centre server. Control centres may be both clients and servers. As such any physical interfaces, transport and network services that fit this model are supported. ICCP may operate over a single point-to-point link between two control centres; however, the more general case is for many control centres and a routed wide area network.
A client may establish associations with more than one server and a client may establish more than one association with the same server. Multiple associations with same server can be established at different levels of quality of service so that high priority real time data is not delayed by lower priority or non real time data transfers. ICCP does not provide authentication or encryption. These services are normally provided by lower protocol layers.
The agreement identifies data elements and objects that can be accessed via the link and the level of access permitted. Once an 608700-6 link is established, the contents of the Bilateral Tables in the server and client provide complete control over what is accessible to each party. There must be matching entries in the server and client tables to provide access to isc and objects.
Although interoperability is not regarded as a high risk area, the standard is such that an implementation does not have to support all conformance blocks in order to claim compliance with the standard. A minimal implementation only requires Block 1.
Only those blocks necessary to achieve the required functionality need be implemented. It is also not necessary to support all objects 600870-6 in the standard for any particular block. Extensive interoperability testing between products of some of the major vendors has been a feature of ICCP protocol development.
Independent reports are available, as no doubt are reports from vendors.
An ICCP purchaser must define functionality required in terms of conformance blocks required and the objects within those blocks. Application profiles for the ICCP client and server conformances must match if the link is to operate successfully. ICCP is a real time data exchange protocol providing features for data transfer, monitoring and control. For a complete ICCP link there need to be facilities to manage and configure the link and monitor its performance.
The ICCP standard iex not specify any interface or requirements for these features that are necessary but nevertheless do not affect interoperability. ICCP implementers are free to handle these issues any way they wish.
Local implementation is the means that developers have to differentiate their product in the market jec added value. Additional money spent on a product with well-developed maintenance and diagnostic tools may well be saved many times over during the life of the product if use of the ICCP connection is expected to grow and change.
This configuration offers maximum performance because of the direct access to the SCADA database without requiring any intervening buffering. This approach may not be available as an addition to a legacy system.
IEC 60870-6 (TASE.2/ICCP)
A networked server making use of industry standard communications networking to the SCADA host may provide performance approaching that of an embedded ICCP application.
On the application interface side the ICCP is not restricted 60870- the SCADA environment but is open to other systems such as a separate data historian or other databases.
Security may be easier to manage with the ICCP server segregated from the operational real time systems. The gateway processor approach is similar to the networked server except it is intended for legacy systems with minimal communications networking capability and so has the lowest performance. From Wikipedia, the free encyclopedia.
This article has ic issues. Please help improve it or discuss these issues on the talk page. Learn how and when to remove these template messages.
This article provides insufficient context for those unfamiliar with the subject. Please help improve the article with a good introductory style. January Learn how and when to remove this template message. This article needs additional citations for verification.
IEC | IEC Webstore
Please help improve this article by adding citations to reliable sources. Unsourced material may be challenged and removed. March Learn how and when to remove this template message. This article may require cleanup to meet Wikipedia’s quality standards. No cleanup reason has been specified. Please help improve this article if you can.
List of International Electrotechnical Commission standards. Retrieved from ” https: Wikipedia articles needing context from January All Wikipedia articles needing context Wikipedia introduction cleanup from January All pages needing cleanup Articles needing additional references from March All articles needing additional references Articles needing cleanup from January Cleanup tagged articles without a reason field from January Wikipedia pages needing cleanup from January Articles with multiple maintenance issues.